To use all functions of this page, please activate cookies in your browser.
With an accout for my.chemeurope.com you can always see everything at a glance – and you can configure your own website and individual newsletter.
- My watch list
- My saved searches
- My saved topics
- My newsletter
Underground storage tank
An Underground Storage Tank (UST), in United States environmental law, is a tank and any underground piping connected to the tank that has at least 10 percent of its combined volume underground. USTs, used to store petroleum, are regulated in the United States to prevent release of petroleum and contamination of groundwater.
Additional recommended knowledge
Underground storage tanks generally fall into three different types:
History of UST regulation in the US
In 1984, in the United States, the Congress developed laws to minimize and prevent environmental damage, by charging owners with the task of verifying, maintaining and, if necessary, cleaning up sites damaged by petroleum contamination.
Legislation requiring owners to locate, remove, upgrade, or replace underground storage tanks became effective December 24, 1989. Each State was given authority to establish a program within its own jurisdiction to set up a program to compensate owners for the cleanup of underground petroleum leaks, to set standards and licensing for installers, and to register and inspect underground tanks.
Most upgrades to USTs consisted of the installation of corrosion control (cathodic protection), overfill protection (to prevent overfills of the tank during tank filling operations), spill containment (to catch spills when filling), and leak detection for both the tank and piping.
Many USTs were removed without replacement during the 10-year program and many thousands of old underground tanks were replaced with newer tanks made of corrosion resistant materials (such as fiberglass) and constructed as double walled tanks to catch leaks from the inner tanks and to give an interstitial space to accommodate leak detection sensors. Piping was replaced during the same period with much of the new piping being double wall construction and made of fiberglass or plastic materials.
Tank monitoring systems capable of detecting leaks as small as 0.1 gallons-per-hour were installed and other methods were adopted to alert the tank operator of leaks and potential leaks.
Regulations included a requirement that UST cathodic protection systems be tested by a cathodic protection expert (minimum every 3 years) and that systems be monitored to ensure continued compliant operation.
Many owners, who previously stored fuel in underground tanks, went to above ground tanks to enable closer environmental monitoring of fuel storage and to reduce costs. Many states, however, do not permit above ground storage of motor fuel for resale to the public.
The USEPA Underground Storage Tank Program is generally considered to have been very successful - with the national inventory of underground tanks reduced by more than half and most of the rest having been replaced or upgraded to much safer standards.
|This article is licensed under the GNU Free Documentation License. It uses material from the Wikipedia article "Underground_storage_tank". A list of authors is available in Wikipedia.|