To use all functions of this page, please activate cookies in your browser.
With an accout for my.chemeurope.com you can always see everything at a glance – and you can configure your own website and individual newsletter.
- My watch list
- My saved searches
- My saved topics
- My newsletter
A Steam accumulator is an insulated steel pressure tank containing hot water and steam under pressure. It is a type of energy storage device which is used to smooth out peaks and troughs in demand for steam in a factory.
Additional recommended knowledge
The tank is about half-filled with cold water and steam is blown in from a boiler via a perforated pipe near the bottom of the drum. Some of the steam condenses and heats the water. The remainder fills the space above the water level. When the accumulator is fully charged the condensed steam will have raised the water level in the drum to about three-quarters full and the temperature and pressure will also have risen.
Steam can be drawn off as required, either for driving a steam turbine or for process purposes (e.g. in chemical engineering), by opening a steam valve on top of the drum. The pressure in the drum will fall but the reduced pressure causes more water to boil and the accumulator can go on supplying steam (at gradually reducing pressure and temperature) for some time before it has to be re-charged.
Pressure and temperature
This steam table shows the relationship between pressure and temperature in a boiler or steam accumulator:
Abbreviations and notes
|This article is licensed under the GNU Free Documentation License. It uses material from the Wikipedia article "Steam_accumulator". A list of authors is available in Wikipedia.|